While many large in-plant office installations will be integrated with centralized HVAC systems, smaller buildings are typically outfitted with wall mounted climate control units. PortaFab will specify the proper unit for your space and then provide wall panels with aluminum-framed cutouts to accommodate the system. These units are typically purchased along with PortaFab's electrical package to ensure that the in-plant office is properly wired.
Standard air conditioning options include complete HVAC systems or air conditioning only systems. Framed cutouts are available for those who want to install their own systems.
To help you estimate the properly sized unit, refer to the following chart that is based on a room with normal insulation and two person occupancy.
|6000 BTU A/C unit.||11,600 BTU combination heater/AC unit.||Larger office structures can be integrated with centralized HVAC systems.|
Example: 20’ x 40’ office = 800 square feet
5 people will occupy the office
Using the chart, 18,000 btu/h are recommended + 500 btu/h for each person over two
Total needed for 800 square foot office with 5 people:
18,000 + 1,500 = 19,500 btu/h
Although HVAC units are available in the above mentioned sizes, it is better to supply two units half the size located at either end of the building to provide more even distribution.
|Baseboard heaters provide a cost effective alternative for some modular offices.|
The most common way to heat a modular office is to include a combination heater/AC unit. Baseboard heaters, however, can also be used. To specify your heating requirements, you can estimate that you will need 7 watts of electric heat per square foot of floor space for a unit with an 8’ ceiling height. The number of watts calculated x 3.4 = total btu’s.
16’ x 16’ office = 256 square feet
256 s/f x 7 watts = 1,792 watts
1,792 watts x 3.4 = 6,092 btu/h
|Standard exhaust fan.|
The amount of ventilation required in an office or building is based on the application of the room as well as the number of expected occupants. For example, a smoking enclosure would require more ventilation than a regular office. The design requirements will either be listed as:
Cubic Foot Requirements – A fractional formula based on .15 cubic foot requirements.
12’ x 12’ x 8’ ceiling = 1,152 cubic feet
1,152 c/f x .15 = 173 CFM’s
A restaurant occupies an average of 50 people. (use the ASHRAE recommended minimum of 35 CFM per person.) 50 people x 35 CFM per person = 1,750 CFM
1,750 CFM/1,000 CFM = 1.75 (1 or 2 units)
Due to the fact that climactic conditions vary so much upon regions and location of the building, it is very difficult to estimate the ideal btu’s needed for each application. Certain conditions, however, will assist in your calculations: